Reasonable price for Signal Conditioner - FC-071 Digital Display Two Step Humidity Controller – Gongyi
Reasonable price for Signal Conditioner - FC-071 Digital Display Two Step Humidity Controller – Gongyi Detail:
1-1、Input type：high molecule
1-3、Display accuracy：±1.0%F.S±1B Sensor accuracy：±3%F.S±1B
1-4、Relay contact capacity：5A 250V AC (Resistance load)
1-6、External dimensions (mm)：76(W)×34(H)×72(D);
hole dimensions (mm)：71(W)×29(H)
1-7、Working power：AC 110～242V 50Hz/60Hz
1-8、Working environment：temperature -20～50℃, relative humidity ≤ 85%RH, without corrode and strong electric radiation.
Ⅱ、The inner parameters：
Ⅳ、The operation illustration：
4-1、Powering on after connecting the controller correctly to according to the connection scheme, the controller starts testing itself for 1 second, then, it displays measured humidity value.
4-2、Humidity setting value set: Press ▲ or ▼ key for 3 second，the set value and “”display by turns，press ▲ or ▼ key to adjust, press SET key to save it and exit. If you do not press any key and wait 10 second, the meter autosave and exit.
4-3、Inner parameters modify:
Press SET key for 3S to enter into the parameters modification status, the parameter code and parameter value display by turns，press ▲ or ▼ key to adjust parameter value, for long time press the key can accelerate. After modification, press SET to save and enter into the next parameter modification status. If you don’t do any operation halfway, the meter will wait 10S, autosave and exit.
When the humidity measured value≥Humidity setting value（）＋Control of return difference（），controller has dehumidifying output (output relay is closed)，the OUT indicator light on； When the humidity measured value≤Humidity set value（）－Control of return difference（），controller has not dehumidifying output (output relay is opened)，the OUT indicator light off；
When the humidity measured value≤Humidity setting value（）－Control of return difference（），controller has humidifying output ( output relay is closed)，the OUT indicator light on；
When the humidity measured value≥Humidity setting value（）＋Control of return difference（），controller has not humidifying output (output relay is opened)，the OUT indicator light off ；
Ⅵ、Wiring diagram (consult)：
When the humidity sensor is beyond testing range or open circuit, the controller will display100”.
Remark：Our company will improve product technology、design and specification continuously. If change, please subject to the material object, without notice.
Product detail pictures:
Related Product Guide:
We stick with the theory of "quality first, company first, steady improvement and innovation to satisfy the customers" for the management and "zero defect, zero complaints" as the quality objective. To perfect our provider, we deliver the items together with the fantastic good quality at the reasonable value for Reasonable price for Signal Conditioner - FC-071 Digital Display Two Step Humidity Controller – Gongyi, The product will supply to all over the world, such as: Porto , Casablanca , Amsterdam , Our company offers the full range from pre-sales to after-sales service, from product development to audit the use of maintenance, based on strong technical strength, superior product performance, reasonable prices and perfect service, we'll continue to develop, to supply the high-quality goods and services, and promote lasting cooperation with our customers, common development and create a better future.
By Gail from Kenya - 2018.06.26 19:27
Speaking of this cooperation with the Chinese manufacturer, I just want to say"well dodne", we are very satisfied.
By Prudence from Washington - 2017.07.07 13:00