Hot-selling Thermostat Regulator With Sensor - FC-040 Single Input Type Intelligent Temperature Controller – Gongyi
Hot-selling Thermostat Regulator With Sensor - FC-040 Single Input Type Intelligent Temperature Controller – Gongyi Detail:
FC1-040 series temperature control meter instruction manual
The meter has international standard external dimension and 3-key gentle push switch setting, single row, 3-LED display: temperature error can correct, the meter has heating or cooling function, you can choice freely. It adopts ON/OFF adjustment, return difference can be adjusted, control precision is high.
1、Input type：NTC10K (B=3380)
2、Temperature display range: －50～150℃
3、Relay output contact capacity：7A 240VAC
4、External dimension(mm)：76×34×72 hole size(mm)：70×28
5、Working power：AC110～242V，50/60HZ, power dissipation is less than 3W
6、Working environment：temperature 0～50.0℃, relative humidity≤85%RH, without corrode and strong electric radiation.
Ⅱ、The inner parameters
Press ▲ or ▼ key for 3 second，the set value and “”display by turns，press ▲ or ▼ key to adjust, press SET key to save it and exit. Or you do not press any key and wait 10 second, the meter auto save and exit.1、Temperature set value set：
2、The second menu parameters modify:
Press SET key for 3S to enter into the second menu parameters modification status, the parameter code and parameter value display by turns，press ▲ or ▼ key to adjust parameter value, for long time press the key can accelerate. After modification, press SET to save and enter into the next parameter modification status. If you don’t do any operation halfway, the meter will wait 10S, auto save and exit.
Heating：（When the parameter of choose ）
When the measured value≤（the set value －return difference value ），OUT relay normally open contact are connected and OUT indicator light is on, the heater is working;
When the measured value≥(the set value ＋return difference value ), OUT relay normally open contact are disconnected and OUT indicator light is out, the heater stop working.
Cooling：(When the parameter of choose )
When the measured value≥（the set value ＋return difference value ），OUT relay normally open contact are connected and OUT indicator light is on, the refrigerator is working;
When the measured value≤(the set value －return difference value ), OUT relay normally open contact are disconnected and OUT indicator light is out, the refrigerator stop working.
4、The meter have refrigeration delay function: When the electricity is on or restart the compressor, need to delay, the delay time is set by the parameter .
Ⅳ、Connection scheme (consult)
Ⅴ、Fault Analysis and Clearance
The meter adopts advanced production process, and have the strict test before leaving factory, it improve the reliability of the meter .The usual fault is caused by the wrong operation or the parameter setting .If you find the fault couldn’t be cope with, please record it, and contact with the agent or us. Sheet 5-1 is the usual fault of the meter in the daily application：
Sheet 5-1 Common fault handling
★Remark：Our company will improve product technology、design and specification. If change, please subject to the material object, without notice.
Attached 1：Statement of meter’s parameter attention letter and English letter
Product detail pictures:
Related Product Guide:
Adhering to the principle of "quality, service, efficiency and growth", we have gained trusts and praises from domestic and international client for Hot-selling Thermostat Regulator With Sensor - FC-040 Single Input Type Intelligent Temperature Controller – Gongyi, The product will supply to all over the world, such as: South Korea , Leicester , Pakistan , Our Company has professional engineers and technical staff to answer your questions about maintenance problems, some common failure. Our product quality assurance, price concessions, any questions about the products, Please feel free to contact us.
By Julie from Monaco - 2018.11.28 16:25
High Quality, High Efficiency, Creative and Integrity, worth having long-term cooperation! Looking forward to the future cooperation!
By Faithe from Hanover - 2017.11.20 15:58