Big discounting Environmental Monitoring Temperature Controller - XMT-607 Series Intelligent PID Humidity Controller – Gongyi
Big discounting Environmental Monitoring Temperature Controller - XMT-607 Series Intelligent PID Humidity Controller – Gongyi Detail:
XMT*-607 series controller is dual row 3-LED display, to display the measured value and set value. It is operated with 3-keys, and the available control methods including on/off, PID control, with easy parameter setting，convenient information inputting and wide voltage power inputting, and so on .
Ⅱ、Main technical Indexes
5、Relay output(passive) contact capacity： AC220V 5A (resistance load)
6、Driving solid relay signal output：Driving electric current＞15mA
floating voltage＞9V，period is 2S
7、Working power：AC85V～242V Power consumption＜3W
8、Working environment：0～50℃, relative humidity≤85％, without corrode and strong electric radiation.
Ⅲ、The meter panel and connection scheme（consult）
★Specific connection should confirm to the controller’s attached
4.1、Electrify after take into the power, sensor and control circuit according to the connection scheme, and then the controller start testing itself for 1 second.
4.2、After testing itself, the controller enter into normal condition, upper row display tested value, underside row SV display the set value.
4.3、Modify the setting value of humidity
Press ▲or ▼key 3 second upper row display tested value, underside row SV display the set value. press▲or ▼key to modify, for long time to press the key can plus or minus the value. After modification, press SET to save and exit .If you don’t press any key for 10s, it will save automatically and exit itself.
4.4、Interior Technical Indexes setting（Technical Indexes refer to the sheet4－1）
Press SET key 3 second enter into the first menu, the upper window display Indexes symbol, underside window displays Index value. Press▲or ▼key to modify，for long time to press the key can plus or minus the value. After modification, press SET to save and enter into next Indexes setting. If you don’t press any key for 10s, it will save automatically and exit itself.
When the power is on, press SET and▼ for 3s to enter the manual adjustment state, the first word in lower row displays “H”, it can set percentage of output power; Press SET and ▼ 3S again can exit manual adjustment state.
Before leaving factory, the meter is set at on/off control,
When the humidity measure value＞setting value＋Hy，the general and lower voltages are disconnected (or solid state relay have no output), OUT indicator bulb is not lighting up;
When the humidity measure value＜setting value－Hy, the meter output connect, OUT indicator bulb light up.
First set the setting value, set “HY” about 0.5～1.0, P is not 0, then set “AT”is ON, and the AT light turn on, the meter enter the setting itself condition, the meter is ON/OFF, After 3 times oscillation，the instrument confirm new P、I、D and so on to save, AT light turn off, the meter reset enter control condition.
Note：①If the power goes off when the meter is setting itself, as the meter with memory function, it will restart setting next time.
②During setting itself, if the setting should be exit artificially, set “AT” is OFF, then can exit, but if that, the setting result will be of no effect.
Ⅶ、Meaning of the model code
XMT □— 6 □ 7 □（1） （2） （3） （4）
（1）: Meter faceplate and Installation dimension(mm)：
Blank: 160×80×85 156×76； A:96×96×80 92×92；
D:72×72×80 68×68； E:48×96×75 44×92
F:96×48×75 92×44 G:48×48×110 44×44
S:80×160×85 76×156 C:80×120×35 Installation mode: Put up
（2）:Operation display method：‘6’3-key gentle push-switch setting，dual row 3-LED display，on/off or PIDcontrol
（3）: Additional alarm:‘blank or 0’ no alarm； ‘1’high limit alarm； ‘2’low limit alarm
（4）：Suffix: blank ：relay output G：Solid state relay output
Ⅷ、Fault Analysis and Clearance
XMT*-607 adopt advanced production process, and have the strict test before leaving factory, it improve the reliability of the meter .The usual fault caused by the wrong operation or parameter setting. If you find the fault couldn’t be cope with, please record it, and contact with the agent or us. Sheet 8-1 is the usual fault of XMT*-607 in the daily application：
Sheet 8-1 Common fault
Attached 1：Statement of meter’s parameter attention letter and English letter
Product detail pictures:
Related Product Guide:
Along with the "Client-Oriented" enterprise philosophy, a rigorous high-quality control process, superior production products along with a robust R&D group, we constantly deliver premium quality products, exceptional solutions and aggressive costs for Big discounting Environmental Monitoring Temperature Controller - XMT-607 Series Intelligent PID Humidity Controller – Gongyi, The product will supply to all over the world, such as: Puerto Rico , luzern , Argentina , All the imported machines effectively control and guarantee the machining precision for the products. Besides, we have a group of high-quality management personnels and professionals, who make the high-quality products and have the ability to develop new products to expand our market home and abroad. We sincerely expect customers come for a blooming business for both of us.
By Antonio from Jordan - 2018.10.09 19:07
The factory technical staff not only have high level of technology, their English level is also very good, this is a great help to technology communication.
By Kim from Macedonia - 2017.02.18 15:54