2017 wholesale price Temperature And Humidity Display - XMT-607 Series Intelligent PID Humidity Controller – Gongyi
2017 wholesale price Temperature And Humidity Display - XMT-607 Series Intelligent PID Humidity Controller – Gongyi Detail:
XMT*-607 series controller is dual row 3-LED display, to display the measured value and set value. It is operated with 3-keys, and the available control methods including on/off, PID control, with easy parameter setting，convenient information inputting and wide voltage power inputting, and so on .
Ⅱ、Main technical Indexes
5、Relay output(passive) contact capacity： AC220V 5A (resistance load)
6、Driving solid relay signal output：Driving electric current＞15mA
floating voltage＞9V，period is 2S
7、Working power：AC85V～242V Power consumption＜3W
8、Working environment：0～50℃, relative humidity≤85％, without corrode and strong electric radiation.
Ⅲ、The meter panel and connection scheme（consult）
★Specific connection should confirm to the controller’s attached
4.1、Electrify after take into the power, sensor and control circuit according to the connection scheme, and then the controller start testing itself for 1 second.
4.2、After testing itself, the controller enter into normal condition, upper row display tested value, underside row SV display the set value.
4.3、Modify the setting value of humidity
Press ▲or ▼key 3 second upper row display tested value, underside row SV display the set value. press▲or ▼key to modify, for long time to press the key can plus or minus the value. After modification, press SET to save and exit .If you don’t press any key for 10s, it will save automatically and exit itself.
4.4、Interior Technical Indexes setting（Technical Indexes refer to the sheet4－1）
Press SET key 3 second enter into the first menu, the upper window display Indexes symbol, underside window displays Index value. Press▲or ▼key to modify，for long time to press the key can plus or minus the value. After modification, press SET to save and enter into next Indexes setting. If you don’t press any key for 10s, it will save automatically and exit itself.
When the power is on, press SET and▼ for 3s to enter the manual adjustment state, the first word in lower row displays “H”, it can set percentage of output power; Press SET and ▼ 3S again can exit manual adjustment state.
Before leaving factory, the meter is set at on/off control,
When the humidity measure value＞setting value＋Hy，the general and lower voltages are disconnected (or solid state relay have no output), OUT indicator bulb is not lighting up;
When the humidity measure value＜setting value－Hy, the meter output connect, OUT indicator bulb light up.
First set the setting value, set “HY” about 0.5～1.0, P is not 0, then set “AT”is ON, and the AT light turn on, the meter enter the setting itself condition, the meter is ON/OFF, After 3 times oscillation，the instrument confirm new P、I、D and so on to save, AT light turn off, the meter reset enter control condition.
Note：①If the power goes off when the meter is setting itself, as the meter with memory function, it will restart setting next time.
②During setting itself, if the setting should be exit artificially, set “AT” is OFF, then can exit, but if that, the setting result will be of no effect.
Ⅶ、Meaning of the model code
XMT □— 6 □ 7 □（1） （2） （3） （4）
（1）: Meter faceplate and Installation dimension(mm)：
Blank: 160×80×85 156×76； A:96×96×80 92×92；
D:72×72×80 68×68； E:48×96×75 44×92
F:96×48×75 92×44 G:48×48×110 44×44
S:80×160×85 76×156 C:80×120×35 Installation mode: Put up
（2）:Operation display method：‘6’3-key gentle push-switch setting，dual row 3-LED display，on/off or PIDcontrol
（3）: Additional alarm:‘blank or 0’ no alarm； ‘1’high limit alarm； ‘2’low limit alarm
（4）：Suffix: blank ：relay output G：Solid state relay output
Ⅷ、Fault Analysis and Clearance
XMT*-607 adopt advanced production process, and have the strict test before leaving factory, it improve the reliability of the meter .The usual fault caused by the wrong operation or parameter setting. If you find the fault couldn’t be cope with, please record it, and contact with the agent or us. Sheet 8-1 is the usual fault of XMT*-607 in the daily application：
Sheet 8-1 Common fault
Attached 1：Statement of meter’s parameter attention letter and English letter
Product detail pictures:
Related Product Guide:
Sticking towards the theory of "Super Good quality, Satisfactory service" ,We are striving to become a superb business enterprise partner of you for 2017 wholesale price Temperature And Humidity Display - XMT-607 Series Intelligent PID Humidity Controller – Gongyi, The product will supply to all over the world, such as: Porto , Los Angeles , Lahore , For anyone who is keen on any of our items right after you view our product list, you should definitely feel absolutely free to get in touch with us for inquiries. You are able to send us emails and contact us for consultation and we shall respond to you as soon as we can. If it's easy, you may locate out our address in our web-site and come to our business for far more information of our merchandise by your self. We're always ready to construct extended and steady co-operation relations with any possible customers in the related fields.
By Audrey from Lahore - 2018.09.29 17:23
The manufacturer gave us a big discount under the premise of ensuring the quality of products, thank you very much, we will select this company again.
By Evangeline from Sevilla - 2018.06.30 17:29