2017 Latest Design Temperature Meter - XMT-JK408 Series Multi Way Intelligent Temperature Controller – Gongyi
2017 Latest Design Temperature Meter - XMT-JK408 Series Multi Way Intelligent Temperature Controller – Gongyi Detail:
XMT*JK four-way temperature controller
XMT*JK four-way temperature controller can connect four sensors synchronously and conveniently, diminish the instrument’s volume. It has a separate auto-tune mode and PID parameter function with more precision and more reliability in whole machine control.
Ⅱ、Primary technical standard:
1、Input signal: CU50（-50.0～150.0℃）、Pt100（-19.9～600.0℃）、K（0～1300℃）、
3、Output method: relay AC220V 3A(resistance load)
4、control mode: difference control-on/off and PID control
5、Input power: AC110~242V 50/60Hz
6、Environment Temperature: 0 to 50℃, Humidity: ≤85%RH
7、Face Size: 160×80×110 mm Hole Size : 152×76 mm 96×96×110 mm Hole Size : 92×92 mm 72×72×110 mm Hole Size :68×68 mm
Ⅲ、Panel board instruction
connection indicator :
PS：1、MiNi printer connection
3、RS232 communication:connect corresponding ‘R’、‘T’、‘GND’.
4、only one function can be used between printer and communication functions at one time.
Ⅴ、Code setting mode
1.Accurately connect uires according as connect indicator,power on.
2.Press ‘SET key’ for 3 seconds,enter into first menu.then ‘parameter ’and paraneter value tims will be shown respectively about ‘CH1 window’ and ‘CH2 window’,you can adjust these parameters by poressing ‘▲’、‘▼’、‘◄’、and save the setting by prwss ‘SET key ’,every parameter should be saved after setting ,then enter next parameter set.
3.You can press ‘CH1’、‘CH2’、‘CH3’、‘CH4’ for 3 seconds to enter into corrseponding channel menu .After finished one parameter set,press ‘SET’ to save it,then enter into next parameter set .
The meter use in the first time or the surroundings have changer, finding it control not good, in this time you need use the setting itself. For example:The first set the AT=1,A-M light flickered, the meter enter into setting itself, press the SET key enter into parameter setting. Set the Hy is 0.5～1℃, if the output is relay set the t=2S, the meter have three times vibrate, automatic preserved P, I, D parameter and the A-M light off, the setting itself finish.
Ⅷ、Fault Analysis and Clearance
XMT*JK408 adopt advanced production process, and have the strict test before leaving factory, it improve the reliability of the meter .The usual fault caused by the wrong operation or parameter setting .If you find the fault couldn’t be cope with, please record it, and contact with the agent or us. Sheet 8-1 is the usual fault of XMT*JK408 in the daily application：
Sheet 8-1 Common fault disposal
★Remark：Our company will improve product technology, design and specification, it is confirm to the object.
Attached 1：Statement of meter’s parameter attention letter and English letter
Product detail pictures:
Related Product Guide:
abide by the contract", conforms on the market requirement, joins within the market competition by its superior quality likewise as provides far more comprehensive and great company for shoppers to let them develop into huge winner. The pursue on the corporation, is definitely the clients' gratification for 2017 Latest Design Temperature Meter - XMT-JK408 Series Multi Way Intelligent Temperature Controller – Gongyi, The product will supply to all over the world, such as: Jordan , Detroit , Stuttgart , We adhere to the honest, efficient, practical win-win running mission and people-oriented business philosophy. Excellent quality, reasonable price and customer satisfaction are always pursued! If you are interested in our products, just try to contact us for more details!
By Karen from luzern - 2018.11.28 16:25
Reasonable price, good attitude of consultation, finally we achieve a win-win situation,a happy cooperation!
By Lynn from Czech republic - 2017.09.26 12:12